Q. What is meant by knee point voltage?
A: Knee point voltage is calculated for electrical Current transformers and is very important factor to choose a CT. It is the voltage at which a CT gets saturated.(CT-current transformer).
Query:What is reverse power relay?
Resolution:Reverse Power flow relay are used in generating stations’s protection. A generating stations is supposed to fed power to the grid and in case generating units are off,there is no generation in the plant then plant may take power from grid. To stop the flow of power from grid to generator we use reverse power relay.
Q:What is the difference between Isolator and Circuit Breaker?
A:Isolator is a off load device which is used for isolating the downstream circuits from upstream circuits for the reason of any maintenance on downstream circuits. it is manually operated and does not contain any solenoid unlike circuit breaker. it should not be operated while it is having load. first the load on it must be made zero and then it can safely operated. its specification only rated current is given.But circuit breaker is onload automatic device used for breaking the circuit in case of abnormal conditions like short circuit, overload etc., it is having three specification 1 is rated current and 2 is short circuit breaking capacity and 3 is instantaneous tripping current.
Q:what is boucholz relay and the significance of it in to the transformer?
A:Boucholz relay is a device which is used for the protection of transformer from its internal faults, it is a gas based relay. whenever any internal fault occurs in a transformer, the boucholz relay at once gives a horn for some time, if the transformer is isolated from the circuit then it stop its sound itself other wise it trips the circuit by its own tripping mechanism.
Q:What is SF6 Circuit Breaker?
A:SF6 is Sulpher hexa Flouride gas.. if this gas is used as arc quenching medium in a Circuitbreaker means SF6 CB.
Q:Tell me in detail about c.t. and p.t. ?(Company:reliance)
A:The term C.T means current transformer,and the term P.T means potential transformer.In circuit where measurements of high voltage and high current is involved they are used there.Particularly when a measuring device like voltmeter or ammeter is not able to measure such high value of quantity because of large value of torque due to such high value it can damage the measuring device.so, CT and PT are introduced in the circuits. They work on the same principle of transformer, which is based on linkage of electromagneticflux produced by primary with secondary.They work on the ratio to they are designed.E.g if CTis of ratio 5000\5A and it has to measure secondary current of 8000A.then ANS=8000*5\5000=8Aand this result will be given to ammeter .and after measuring 8A we can calculate the primary current.same is the operation of PT but measuring voltage.
Q:Explain the working principal of the circuit breaker?
A:Circuit Breaker is one which makes or breaks the circuit.It has two contacts namely fixed contact & moving contact.under normal condition the moving contact comes in contact with fixed contact thereby forming the closed contact for the flow of current. During abnormal & faulty conditions(when current exceeds the rated value) an arc is produced between the fixed & moving contacts & thereby it forms the open circuitArc is extinguished by the Arc Quenching media like air, oil, vaccum etc.
Q:What is the difference between surge arrestor and lightning arrestor?
A:LA is installed outside and the effect of lightning is grounded,where as surge arrestor installed inside panels comprising of resistors which consumes the energy and nullify the effect of surge.