Query:What is the count of hvdc transmission lines in India?
Resolution:At present there are three hvdc transmission lines in india
1)chandrapur to padghe(mumbai)–(1500 MW at ±500 kV DC)
2)rehand to delhi (1500 MW at ±500 kV DC)
3)talchal to kolar (2500 MW)
Query:What is meant by regenerative braking?
Resolution:When the supply is cutt off for a running motor, it still continue running due to inertia. In order to stop it quickly we place a load(resitor) across the armature winding and the motor should have maintained continuous field supply. so that back e.m.f voltage is made to apply across the resistor and due to load the motor stops quickly.This type of breaking is called as “Regenerative Breaking”.
Query:Why is the starting current high in a DC motor?
Resolution:In DC motors, Voltage equation is V=Eb-IaRa (V = Terminal voltage,Eb = Back emf in Motor,Ia = Armature current,Ra = Aramture resistance). At starting, Eb is zero. Therefore, V=IaRa, Ia = V/Ra ,where Ra is very less like 0.01ohm.i.e, Ia will become enormously increased.
Query:What are the advantages of star-delta starter with induction motor?
Resolution:(1). The main advantage of using the star delta starter is reduction of current during the starting of the motor.Starting current is reduced to 3-4 times Of current of Direct online starting.(2). Hence the starting current is reduced , the voltage drops during the starting of motor in systems are reduced.
Query:Why Delta Star Transformers are used for Lighting Loads?
Resolution:For lighting loads, neutral conductor is must and hence the secondary must be star winding. and this lighting load is always unbalanced in all three phases. To minimize the current unbalance in the primary we use delta winding in the primary. So delta / star transformer is used for lighting loads.
Query:Why in a three pin plug the earth pin is thicker and longer than the other pins?
Resolution:It depends upon R=rho l/a where area(a) is inversely proportional to resistance (R), so if (a) increases, R decreases & if R is less the leakage current will take low resistance path so the earth pin should be thicker. It is longer because the The First to make the connection and Last to disconnnect should be earth Pin. This assures Safety for the person who uses the electrical instrument.
Query:Why series motor cannot be started on no-load?
Resolution:Series motor cannot be started without load because of high starting torque. Series motor are used in Trains, Crane etc.
Query:Why ELCB can’t work if N input of ELCB do not connect to ground?
Resolution:ELCB is used to detect earth leakage fault. Once the phase and neutral are connected in an ELCB, the current will flow through phase and that much current will have to return neutral so resultant current is zero. Once there is a ground fault in the load side, current from phase will directly pass through earth and it will not return through neutral through ELCB. That means once side current is going and not returning and hence because of this difference in current ELCB wil trip and it will safe guard the other circuits from faulty loads. If the neutral is not grounded, fault current will definitely high and that full fault current will come back through ELCB, and there will be no difference in current.
Q:How electrical power is generated by an A.C Generator?
A:For the generation of elect power we need a prime mover which supplies mechanical power input to the alternator, can be steam turbines,or hydro turbines .When poles of the rotor moves under the armature conductors which are placed on the stator ,field flux cut the armature conductor ,therefore voltage is generated and is of sinusoidal in nature…due to polarity change of rotor poles(i,e) N-S-N-S.
Q:Why an ac solenoid valve attract the plunger even though we interchanges the terminal? Will the poles changes?
A:Yes because the poles changes for every half-cycle of ac voltage so the polarity of AC voltage is continuously changing for every half cycle. so, interchanging of terminals in ac system does not show any difference. That’s why the ac solenoid attract the plunger even though it’s terminals are interchanged.
Q:What is derating?, why it is necessary, it is same for all means for drives, motors,and cables.
A:The current currying of cables will change depending upon the site temperature (location of site), type of run (it will run through duct, trench, buried etc.), number of tray, depth of trench, distance between cables. Considering this condition actual current currying capacity of cable reduce than current currying capacity (which given to cable Catalogue) this is called derating.
Q:Why temperature rise is conducted in bus bars and isolators?
A:Bus bars and isolators are rated for continuous power flow, that means they carry heavy currents which rises their temperature. so it is necessary to test this devices for temperature rise.
Q:When voltage increases then current also increases then what is the need of over voltage relay and over current relay? Can we measure over voltage and over current by measuring current only?
A:No.We can’t sense the over voltage by just measuring the current only because the current increases not only for over voltages but also for under voltage(As most of the loads are non-linear in nature).So,the over voltage protection & over current protection are completely different. Over voltage relay meant for sensing over voltages & protect the system from insulation break down and firing.
Over current relay meant for sensing any internal short circuit, over load condition ,earth fault thereby reducing the system failure & risk of fire.So, for a better protection of the system.It should have both over voltage & over current relay.
Q:If one lamp connects between two phases it will glow or not?
A:If the voltage between the two phase is equal to the lamp voltage then the lamp will glow. When the voltage difference is big it will damage the lamp and when the difference is smaller the lamp will glow depending on the type of lamp.